Create an Account - Increase your productivity, customize your experience, and engage in information you care about.
The GFCI outlet must be at least 5 feet from the inside wall.
Show All Answers
Smoke detectors are required in all bedrooms, hallway outside of bedroom, one on each floor.
Carbon Monoxide Detectors are required in bedroom hallways.
A ground rod wire never has to be larger than a Number 4 copper. It cannot be smaller than Number 4 if it is subject to physical damage.
The size is Number 4 copper or Number 2 aluminum.
The size is Number 2-O copper or Number 4-O aluminum.
Street lights are not our jurisdiction, call Ohio Edison at 800-633-4766. We only maintain Traffic signals.
PVC conduit must be 18 inches deep.
Yes, but they must be type S so a larger fuse cannot be installed.
They are required in all:
It means arc fault circuit interrupter.
It trips on inline arcs such as broken ripcords, loose connections, etc.
The water ground connection has to be within 5 feet of the water service entering the house.